Modular Environmental Control Unit (MECU)
Mainstream's MECU is designed to provide cooling, heating and ventilation to the Tent Extendable Modular Personnel (TEMPER), Modular General Purpose Tent System (MGPTS) or CP EMEDS shelters. A single MECU has sufficient capacity to provide thermal control to shelters as large as 1,000 square feet in ambient temperatures as high as 130°F or as low as - 40°F. The MECU allows for air plenum configuration and installation requirements without bends in the supply or return ducts. The MECU has been designed to replace both the FDECU, LECU and the IECU with a smaller cube, improved performance, reduced weight, improved power-factor and improved maintenance/reliability.
|Dimensions/Weight||Center of Gravity|
|Width||51.5 inches (130.8 cm)||27.4 inches|
|Depth||41.6 inches (105.6 cm)||25.0 inches|
|Height||31.6 inches (80.3 cm)||16.4 inches|
|Weight||MECU-410 660 lbs (299.4 kg) / MECU-290 653 lbs (296.2 kg)|
(125° F Ambient)
|Power Requirements||13 kW||17.5 kW|
|Max. Running Amperage||40 Amps||45 Amps|
|Max. Inrush Current||200 Amps||80 Amps|
|Refrigerant Capacity||12 lbs||5.5 lbs|
|Cooling Capacity||60,000 Btu/hr
@ 125° F d.b. ambient temperature with return temperature of 90°F d.b./75°F w.b.
|Heating Capacity||One-Stage 6 kW (Set-point <80°F and return air temp >70°F)
Two-Stage 12 kW (Set-point >80°F or return air temp < 70°F)
|2,000 SCFM airflow at 3” H20 head pressure|
This product was developed under an SBIR contract.
Any Federal agency may procure these units at any time without further competition. The competition for SBIR Phase I and Phase II awards satisfies any competition requirement when processing Phase III awards. Therefore, an agency is not required to conduct another competition in order to satisfy any statutory provisions for competition. This is authorized under 10 U.S.C. 2304(b)(2) or 41 U.S.C. 253(b)(2). A separate J&A document is not required, pursuant to 10 U.S.C. 2304(b)(3) or 41 U.S.C 253(b)(3).
® 2010 MAINSTREAM ENGINEERING CORPORATION